Emptying tankers can cause problems for many pumping processes.
The difficulties involved are air pockets which cannot be avoided when attaching a pipe. The gas bubbles initially lead to reduced performance and irregular running until the product flow stalls as the gas inflow further increases.
The product flow used to stall again and again during the emptying of the surfactant with the centrifugal pump that was used before. The centrifugal pump was intended to convey the basic material of the detergent from a road tanker to the company's production facility. However, problems arose as early as the suction phase: air which got into the pipe during connection of the tank formed air pockets in the medium. This led to slumps in performance and also to repeated stalling of the product flow. The pump kept on breaking down and had to be recommissioned, involving a great deal of effort from the personnel. Tanker drivers were often obliged to suffer a long unscheduled wait until the tank was empty, which meant high additional costs for hazardous goods carriers who have to adhere strictly to driving and rest times.
The surfactant being conveyed was diluted with a solvent in this application. Most plastics are not resistant to solvents and elastomer swells in contact with them and impairs pump performance. For this reason, the all-metal model of the T.Proc® made of stainless steel was installed. This type of TORNADO® rotary lobe pump enables to guarantee a long service life for all parts that come into contact with the product. A special universally usable elastomer was used for the seals which has high chemical and temperature resistance due to its composition. As the pump operates in an area which is designated as an explosion protection area 1, the pump must not run dry under any circumstances. For this reason, both pressure and dry running protection were integrated so that the pump automatically switches off in the event of a fault. The positive displacement pump has now been running trouble-free since the end of October 2013 and conveying 15 to 20 m³ of surfactant per hour at a pressure of 4 bar.
Meanwhile, there is no longer need for supervisory staff during the emptying of the tanker thanks to this high level of reliability and drivers can easily start the process themselves and complete it within the scheduled time frame. Additional costs for waiting times, production downtimes and the staff effort involved in recommissioning the centrifugal pump are a thing of the past.
|NETZSCH||TORNADO® T.Proc rotary lobe pump|
|Throughput volume||15 to 20m³/h|
|Viscosity||Up to 50.000 cP|